What is the maximum and minimum power admitted in the channel of Luzen Plus?
The acceptable range in the output of the dimmer channel for proper operation is:
- [50W.......400W] for resistive, capacitive and inductive loads.
- [5W......125W ] for dimmable LED lamps and dimmable compact fluorescent lamps (CFL)
What kind of load can I connect to the dimming channel of Luzen Plus?
Resistive, capacitive, inductive, dimmable LED and CFL loads can be connected to the dimming output of Luzen Plus (230V AC).
To control dimmable CFL and LED lamps it is necessary to download the application program version Luzen Plus 3.0 or higher
There is a problem with the load in the Luzen Plus. How can I identify the problem?
In Luzen Plus you can enable different communication objects that allow us to identify problems in the device or the installation itself:
- Short circuit
- Open Circuit
- Anomalous Frecuency
To use these objects, it will be necessary to have five different group addresses conveniently linked with the above objects.
Which Zennio products have logical functions?
- Actuators (all): MAXinBOX SHUTTER 8CH, MAXinBOX SHUTTER 4CH, MAXinBOX 16 Plus, MAXinBOX 16, MAXinBOX 8 Plus, MAXinBOX 8, MAXinBOX 66, MINiBOX 45, MINiBOX 25, MINiBOX Quatro, MINiBOX 20, inBOX 24, inBOX 20, ACTinBOX MAX 6, ACTinBOX QUATRO, ACTinBOX Classic Hybrid.
- Lighting: DIMinBOX DX2, DIMinBOX 2CH, Luzen Plus, Luzen One
- Clima: MAXinBOX Hospitality, MAXinBOX FANCOIL 4CH2P, MAXinBOX FANCOIL 2CH2P, MAXinBOX FC 0-10V FAN, MAXinBOX FC 0-10V VALVE, HeatingBOX 230V 8X, HeatingBOX 230V 4X, KLIC-DD, KLIC-DI Sky, ACTinBOX MAX 6 Fan Coil y ACTinBOX QUATRO Fan Coil.
- KNX Energy Saver: KES, KCI.
Can I use the same Logical Function variables in different operations?
Yes, this is possible; just have on mind that the value stored in the variable changes when executing any operation in which it is involved, and this inevitably will affect the rest of operations using this same variable.
Is the value of an internal variable retained between different calls to the logical function?
Yes, it is. The value is retained even after a power failure, and it can also be used in different logical functions.
Is it possible to enchain several logical functions to solve complex issues?
Yes, it is. If the same object is used to call several functions, they will be executed in order, and it is also possible to pass values from one function to another using the internal variables.
All my Group Address associations with the Logical Function Communication objects disappeared. What happened?
This happens in the modules of 5 logical functions, where you need to input the number of Total Data Entry objects of each type in parameters. If you need to increase those parameters of Total Data entry objects onces you have made all the Logical Function Group Address associations, you will lose those associations.
WE ALWAYS RECOMMEND to define some more additional objects than the strictly necessary in the Logical Functions, as a later redefinition involves the deletion of the possible Group Address associations already made, with the consequent loss of time when having to associate them again.
In the modules of 10 logical functions, each Data Entry is enabled independently, avoiding the lose of associations when you need a different number of Data Entry objects.
What is Luzen PLUS?
Luzen PLUS is a step forward in the evolution of our (1 channel, 400W) Luzen ONE dimmer. Luzen PLUS (ZN1DI-P400) has been subject to hardware updates regarding the Luzen ONE (ZN1DI-4001).
What is the main difference between Luzen ONE and Luzen PLUS?
Luzen PLUS offers auto load detection in the dimmer channel while in the Luzen ONE this has to be manually set by a specific parameter included in the application program.
Moreover, Luzen Plus control dimmable CFL and LED lamps with the version of application program Luzen Plus 3.0 or higher.
Do the clamps or the wiring change in the Luzen PLUS?
No, both the clamp and the wiring are identical in the Luzen ONE as well as in the PLUS.
Why does the "load type" parameter disappear?
Due to the hardware update carried out in the Luzen Plus, this is now able to automatically detect the type of load so that the specific parameter is not needed any more.
How can I tell if my dimmer is a Luzen ONE or a Luzen PLUS?
The own silkscreening in the device shows if it is a Luzen ONE or a Luzen PLUS.
In addition, the product code is different:
Luzen ONE code: ZN1DI-4001,
Luzen PLUS code: ZN1DI-P400.
Will you still support the Luzen ONE application program?
Yes, the Luzen ONE application program will be normally supported, all the files and info regarding this product will be available in its web section.
Is the Luzen ONE application program compatible with the Luzen PLUS?
No, the Luzen ONE has a specific application program which is not compatible with the Luzen PLUS, and vice versa.
Where can I find info regarding these two products?
In www.zennio.com, every device is covered in different sections , just like two different products , where you can find all the info regarding both.
What does safe mode mean?
When a device is running in safe mode the programming LED blinks in red, meaning that the application program is halted.
How to set a device in safe mode?
To activate the safe mode, keep the programming button pressed while connecting the device into the KNX bus. This process is described in the datasheet of the device.
How to exit from safe mode?
To exit from safe mode, simply plug the KNX bus into the device but do not press the programming button this time. This way the programming LED does not blink, meaning that the application program is running (safe mode is not active).
How do a download in safe mode?
When an incidence is caused during the download, it is recommended to do a safe mode download, to ensure that the previous corrupted download doesn’t affect to this new download:
To do a download in safe mode, you should follow the next steps:
- Disconnect the device from KNX bus.
- Connect the device to KNX bus while holding down the programming button. The programming LED will start blinking indicating that the device is in safe mode.
- Once in safe mode, download the application program completely to the device.
- When the download is finished, disconnect and reconnect the device from the bus.